||Building Materials Manufacturing Corp.
|Cause of Order
||incurred a Failure to Monitor for microbiological quality; incurred a Failure to Monitor for trigged ground water source monitoring; incurred an E. coli MCL violation; screened riser pipe on Facility well had not been covered or sealed to protect well from contamination
|Requirements of Order
||Comply with Rules; provide Tier 3 public notification; connect Facility to the nearest available municipal public water supply system; secure the serives of a qualified storage tank company and conduct a thorough and comprehensive inspection of Facility's elevated storage tank; submit a Corrective Action Plan and implement; submit a final written certification of completion documenting the actions taken
||Safe Drinking Water Act